Product Specifications. • 9th edition approved UL • Capacity of up to 64 panels with zones of programming through software. • Powerful and versatile . FireNET FN/FN UL/FM approved. Expandable loop and connect to other panel. ANALOG ADDRESS FIRE CONTL PAN, Hochiki. Description: Analog Address Fire Contl Panel; Category: Addressable Panels, Fire Control Panels, Fire; UPC.
|Published (Last):||25 January 2005|
|PDF File Size:||11.91 Mb|
|ePub File Size:||18.59 Mb|
|Price:||Free* [*Free Regsitration Required]|
Hoochiki I dont want to use som also I want to install many horn within a panel which will work automatically. Can you give me a diagram of your suggestion? That is not legal and could put you and your employer in jeopardy.
One NAC at 1. The ones made by Hochiki are controlled and supervised by a NAC from the main panel.
Hochiki | Brands | Moxee Electronics Inc. | Page 5
The device address is uniquely stored on an onboard. Again, the amount of devices depends on the device’s rating, wire gauge, current draw of each device, etc Also i know that will not supervised. The communicator may be configured to report by zone or by address point. Post Mon Mar 20, 6: Home Shop Store Contact us. I am just stared learning the system. Post Mon Feb 27, 5: For manual call point placement inside SLC loop what control module is used?
FireNET® Intelligent Addressable, 2 Loop, Red, 120V
Post Thu Mar 02, In the control panel there is 4 NAC connection points. NAC only can supply 4 amp only.
With 4 amp current we can only connect a few horn strobe. Because the NAC extender has its own power supply it does not draw power from the gn-2127 panel. It provides two independent contact monitoring circuits while only utilizing one address on the SLC loop. Very rarely will you find configurations with more than this. Depends on a lot of variables, including the wire gauge, wire length, and current draw of each device as well as the limitations of each NAC and combined NAC’s.
Only to supervise notification devices? From the Firenet installation manual: These outputs may be used for a variety of purposes including door holders, elevator recall, and other fire safety functions.
If i use a automatic Sprinklers system then the basic is if there is a fire then detectors detects and send a signal to control panel that there is a fire, then control panel send a signal to notification devices to alarm. Post Wed Mar 01, 1: These are a separate box with a power supply, battery charger, batteries, and NACs. Thanks for your reply. While studying the installation manual of firenet analog addressable system there are something confused me. The module allows the panel to interface and monitor two-wire conventional detectors or pull stations.
Post Sun Mar 19, 6: Can i directly connect sounder base in a SLC loop? As NAC generate power, if i use this power to operate a relay which is already connected with external power supply. User Control Panel Profile Logout. The FNSLC can be added at the factory or installed in the field, and mounts within the main control board location as a piggy-back board. I know this is illegal.
Hochiki fire alarm center FN / FN
The SOM provides a supervised 24VDC polarity reversing output on the SLC loop most commonly used for audible and visual signaling ohchiki or triggering a remote notification appliance circuit power expander.
As it says in the manual about the SOM: Post Wed Mar 01, 7: Dome Camera p Turbo HD, 2. That means i 4 loop of NAC devices? But what i posted will it work or not?